- Open Access
Damage event analysis of vertical ground source heat pump systems in Germany
© The Author(s) 2017
- Received: 11 April 2017
- Accepted: 20 June 2017
- Published: 29 June 2017
In recent years, some spectacular cases of damage occurred with vertical ground source heat pump (GSHP) systems in Germany. Broad media coverage attracted enormous public attention, with reports about land subsidence and ground uplifts causing severe damage to buildings. Consequently, sales of vertical GSHP systems have declined. The current study develops conceptual models illustrating the causes and effects of damage in relation to geological and hydrogeological settings. Our investigations revealed nine cases of serious damage in Germany, causing financial losses of more than 100 million Euros. In most cases, connection of aquifers by leaky annular space grouting was the main cause of damage. Guidelines to regulate the installation of vertical GSHP systems have been introduced successfully in all federal states. However, further risk minimisation strategies must be developed to restore the public’s confidence in GSHP technology. Quality assurance and quality control measures should include in particular the optimisation of backfilling materials and increasing use of monitoring systems.
- Ground source heat pumps
- Ground heaving
- Damage event analysis
- Shallow geothermal energy
Change in hydraulic, geophysical, and geochemical parameters caused by the hydraulic connection of separate aquifers.
Destabilising effect of ascending groundwater flows on the backfilling (AD-HOC-AG Geologie 2011).
Flooding of adjacent buildings and infrastructure by artesian discharge.
Swelling or subrosion processes of sulphate- and salt-bearing layers, leading to subsidence or ground uplifts.
The formation of sinkholes or the loss of drilling equipment in karst areas (Butscher et al. 2010).
Creation of new migration pathways for physical and chemical contaminants, such as organic anti-freeze liquids, diffusing chemicals in the backfilling material or contaminated drilling fluids (Klotzbücher et al. 2007; Santi et al. 2005).
Potential hazards for drilling teams and residents due to near-subsurface gas reservoirs (Sachs and Eberhard 2010).
High pollution vulnerability of groundwater in the area around contaminated sites.
According to the current industry report of the Federal Association of GSHP, sales figures will increase again until 2030, despite the population’s loss of trust in the technology (BWP 2016). The expected sales upturn will be due to increased governmental subsidies for the installation of GSHP systems. In order to exploit the expected market momentum, minimising risks is of highest priority. Each subsurface activity affects the environment, and the probability of hazardous events increases with the number of drillings. Based on a previous study by Grimm et al. (2014), damage event analysis of vertical GSHP here is extended to cover entire Germany. The objective of the present study is to identify causes and effects of past damage events and to develop conceptual failure models considering local geological and hydrogeological subsurface conditions. Furthermore, occurrence probability of damage events in Germany is determined. Based on the analysis, we will discuss quality assurance measures for safer operation of vertical GSHP systems in the future.
So far, no official statistics on damages caused by GSHP systems in Germany have been published (Schäfer and Rumohr 2011). GSHP projects are legally approved of and controlled by local water authorities (Hähnlein et al. 2011). Damages that do not manifest on the surface or only occur long after the installation often remain undetected. Owners and drilling companies usually handle minor incidents among themselves. They often do not inform the responsible authority. Typically, local water authorities only consult State Geological Surveys (SGD) in specific cases, when a detailed cause-and-effect analysis is required (AD-HOC-AG Geologie 2011). Consequently, it is not possible to provide a reliable and comprehensive statement regarding the number of unreported damage events in Germany. Since information is provided in case of spectacular events only, this study focusses on cases with losses exceeding 500,000 Euros only.
Information on damage events was obtained from written enquiries to all federal geological surveys, from geological status reports, and from press releases. Additionally, the investigations of Grimm et al. (2014) provided a detailed overview of damage events during the drilling of borehole heat exchangers (BHE) in the state of Baden-Württemberg. The Geology AD-HOC Commission published a report on known impacts of shallow geothermal energy in Germany (AD-HOC-AG Geologie 2011). In this report, effects that are expected, accepted effects, and effects that occur unexpectedly are distinguished. Unexpected effects do not only include cases of high damage costs, but also impacts on the environment that cannot be quantified or temporary impacts, such as polluted water bodies or changed chemical and physical groundwater properties. Negative impacts most often refer to groundwater quality. In addition, there can be severe effects at the surface, such as ground uplifts, subsidence, or flooding.
Serious damage events (>500,000 Euros) of vertical GSHP projects in Germany
Damage in million (Euros)
Causes and effects
Subrosion of sulphate-bearing layers due to connection of aquifers resulting in subsidence
Ingress of ascending/descending groundwater into anhydrite-bearing layers resulting in ground heaves at the surface
Ingress of ascending groundwater into anhydrite-bearing layers resulting in ground heaves at the surface
Ingress of descending groundwater into anhydrite-bearing layers resulting in ground heaves at the surface
Connection of aquifers with descending groundwater potential due to a leaky backfilling. Land subsidence due to decreasing groundwater level
Drilling into karst structures. Descending, vertical groundwater flow, and material transfer. Sinkhole and subsidence at the surface
Tapping of an artesian aquifer. Flooding at the surface
Connection of aquifers with descending groundwater potential due to a leaky backfilling. Land subsidence due to decreasing groundwater level
No specific causes are identified yet
In September 2008, two drillings were made for the installation of a vertical GSHP system in Böblingen, a town southwest of the state capital of Stuttgart. In late 2011, fine cracks appeared in the walls of several buildings (Fig. 3a). Geodetic measurements on behalf of the LGRB identified two uplift areas. In January 2014, the total uplift was measured to be 37–45 cm in the northern and 25–30 cm in the southern body after a period of 3 years (LGRB 2016).
To identify the cause of damage, the LGRB made several exploration drillings. Similar to the case of Staufen, inflow of groundwater into an anhydrite-bearing layer had caused the uplifts. The swellable anhydrite layers were located in the Grabfeld formation at a depth of 56–114 m below ground level (Fig. 4). Geothermal drillings reached their final depth in the impermeable Erfurt formation. Hence, upward migration of the underlying confined groundwater of the Upper Muschelkalk was excluded just as in the city of Staufen. Temperature profiles confirmed a descending groundwater flow from the Stuttgart formation into the anhydrite-bearing layers of the Grabfeld formation. Groundwater from the Stuttgart formation found its way through a leaky backfilling. In late 2014, the LGRB took first damage-limiting measures: Post-grouting of the leaky annulus with sulphate-resistant cement and permanent groundwater drawdown below the swellable zones. After this, the temperature profiles indicated a stop of vertical groundwater flow along the installed BHE. A reduced ground uplift rate was measured as soon as the initial recovery measures started (LGRB 2016). The uplift damaged more than 250 buildings and the amount of damage is currently estimated to be around 50 million Euros (StZ 2015).
In Kamen-Wasserkurl, in the state of North Rhine-Westphalia, a borehole was drilled for geothermal energy supply of a detached home in 2009. When drillings reached a depth of 70 m, the drilling team stopped the work in the late afternoon. Later on the same day, a sinkhole formed around the drilling site. The sinkhole had a volume of 50–60 m3 and buried the entire drilling equipment. On the following days, a land subsidence of up to 10 cm was measured up to a distance of 200 m from the drilling site. Cracks started to appear in adjacent buildings. Twenty neighbouring houses were damaged and four of them finally had to be demolished (AD-HOC-AG Geologie 2011). With a final depth of 70 m, drillings had reached the transitional zone between the Emscher formation and the karstified Plänerkalk group (Fig. 4). The Emscher formation and particularly the Plänerkalk group are characterised by water-conducting faults that are interconnected with the karst system of the Plänerkalk group (AD-HOC-AG Geologie 2011). Low volumes of cuttings indicated a loss of drilling fluid during the drilling process already. The cuttings were flushed into the karst system by the drilling fluid. The loss of drilling fluid went unnoticed at the surface: groundwater flow from the quaternary aquifer into the borehole compensated the loss of drilling fluid. Groundwater flow was facilitated by the absence of an annulus casing. When the drilling team pulled out the pipes in the evening, groundwater flow was reinforced. With increasing flow velocities, large amounts of sediment were eroded and transported into the karst formation. A sinkhole formed around the uncased annulus. At a certain point, the material loss was balanced by a lateral mass transfer from the quaternary aquifer. This subrosion process led to subsidence in the surrounding area. The borehole was grouted with 750 m3 of cement in the following 3 months. The hydraulic sealing of the quaternary aquifer and the karst formation could be restored. The total amount of damage is presently estimated to be more than one million Euros (WN 2009).
In November 2009, drilling activities for a near-surface geothermal energy application on behalf of the Hessian Ministry of Finance induced flooding in the city centre of Wiesbaden. Drillings reached a depth of 130 m when a 7-m-high groundwater spring erupted from the borehole. Up to 6000 l/min of groundwater poured over a 400 m2 large area around the drilling site (Fig. 3c). Even though the borehole was filled with 56 m3 cement late at night, water discharge could not be stopped. New springs were formed in the vicinity of the borehole. At a depth of 130 m, the exploration drilling hit an artesian aquifer (Fig. 4). With the discharging water, large amounts of loose material were flushed out of the ground. Due to potential subrosion processes, there was an increased hazard of land subsidence. Seismic follow-up investigations, however, did not show any irregularities in the subsurface. The costs of damage were estimated to be 500,000 Euros (FAZ 2010).
In October 2016, a borehole was drilled for the installation of a vertical GSHP system in Rottach-Egern (Bavaria). When drillings reached a depth of 45 m, a 20-m-wide and 2-m-deep sinkhole started to appear (Fig. 3d). Only little information is available about the cause and processes of subsidence. According to first assumptions, drillings hit a groundwater-filled subsurface cavity. The cavity is a relic of a buried ice block formed by landslides during glacial periods (TS 2016). Damage is estimated to be 500,000 to one million Euros.
On the international level, hardly any information is available on damages caused by vertical GSHP systems. Similar to the cases of Staufen and Böblingen, anhydrite swelling damaged more than 100 historic houses in the town of Lochwiller, France. In Switzerland, Bassetti et al. (2006) reported several minor damages, such as subsidence or demolished probes.
In addition to the nine cases of damage exceeding 500,000 Euros described above, there were further cases with minor or non-quantifiable damage. These included flooded properties, polluted surface water bodies, dried-up wells, and changed chemical and physical groundwater properties (AD-HOC-AG Geologie 2011). However, there are no statistics about the frequency of such cases. According to a first estimation, the probability of damage with an amount of more than 500,000 Euros was calculated to be 0.0001% per year. This calculation is based on more than 350,000 installed GSHP systems in Germany over the last 26 years (Fig. 1 with data from BWP 2016). There are no official figures relating to the percentage of installed vertical systems out of the total number of installed GSHP. According to Walker-Hertkorn (personal communication 2017), the proportion of vertical systems is about 80%.
In general, usage and installation of vertical GSHP systems in Germany can be considered fairly safe compared to other technologies. Figure 6 compares the probability of a serious damage event of vertical GSHP with the probability of dying from air pollution caused by coal-fired plants in Germany [0.003% per year (Grimm et al. 2014)] and the probability of a serious accident at a nuclear reactor worldwide [0.02% per year (Grimm et al. 2014)]. Even though the idea of this comparison is to emphasis the low probability of serious damage events in Germany, the higher energy output of fossil-based energy sources is obvious.
As a consequence of hard coal mining, 35,000 claims for damages are made annually against the RAG AG, the largest German coal mining corporation (RAG 2014). Although 90% of these claims are below 5000 Euros, the lifecycle costs of anthracite coal mines are estimated to be 13 billion Euros (RAG-Stiftung 2015). Even though the probability of serious damage events of vertical GSHP systems in Germany is rather low, such cases have to be prevented to restore public confidence in this renewable energy technology.
In Germany, standardised mining and water law approval procedures for vertical GSHP systems exist neither on the national, nor on the state level (Kübert et al. 2009). There is no specific law that governs the handling of shallow geothermal energy in Germany. Legal frameworks are derived from the Water Act and the Mining Act (Hähnlein et al. 2011). Guidelines adopted by each federal state complement the legal provisions (BVG 2014). Kübert et al. (2009) highlighted the differences of approval procedures between the federal states and national states (Hähnlein et al. 2011). Legal regulations differ considerably from state to state. The state of Baden-Württemberg reacted to the damage events by taking measures to assure quality as outlined in the “guidelines for quality assurance of downhole borehole heat exchangers” (LQS EWS 2011). For example, these guidelines require proof of suitability of the backfilling material used by an accredited institution. In case of confined groundwater conditions, packer systems have to be on hand to prevent uncontrolled groundwater discharge. Drilling depth is limited in case of anhydrite-bearing layers in the subsurface. Also material, technical, and anthropogenic issues are considered. The LQS EWS guidelines introduced have already proven their effectiveness: In all cases of damage known in Baden-Württemberg, the BHE had been installed prior to the publication of the LQS EWS.
The LQS EWS demonstrated the importance of considering regional boundary conditions when implementing national laws. Butscher et al. (2010) presented a risk-oriented approach to the approval of BHE in the Canton of Basel-Landschaft, Switzerland. It is important to also consider local and specific risks during the approval process. Hence, all geological, hydrogeological, geotechnical, and anthropogenic hazards have to be identified. By integrating all factors into a geographic information system (GIS), authorities, drilling companies, and owners are able to estimate the hazard potential of each project. In most federal states, such a GIS has already been established (e.g. Ondreka et al. 2007). The “information system on shallow geothermal energy in Baden-Württemberg (ISONG)” launched by the LGRB is a successful example: the online map does not only show water protection areas, but also warns of confined aquifers as well as geological difficulties. The Leibniz Institute for Applied Geophysics is also setting up an internet-based information system of geothermal resources for the entire country (Schulz et al. 2007). Currently, this effort focusses on providing information about geothermal potentials. Possible risks are not yet displayed. The project “Shallow Geothermal Energy Planning, Assessment and Mapping Strategies in Central Europe (GeoPLASMA-CE)” generates a cross-national web-based platform, which provides tools to support decision making and enables a visualisation of geothermal potentials and risks of conflicts. Based on current projects, a platform for comprehensive information on potential geological risks is expected to be established in the future.
To prevent future damage, qualitative improvement of applied materials and working processes must have priority. The Hydrogeology AD-HOC Committee has developed a range of quality assurance measures and published them in a technical report (AD-HOC-AG Hydrogeologie 2015). Different drilling methods, frost resistance and longevity of backfilling materials, and several monitoring systems were tested. Furthermore, Solites, Karlsruhe Institute of Technology, and the EIFER Institute conduct research for the development of vertical GSHP systems within the framework of the EWS-tech project (Riegger et al. 2016). They chose a three-stage approach of laboratory, small-scale, and real-scale experiments. Based on the outcome of the experiments, recommendations for improved grouting of BHE are made, which can also be included in official guidelines. Thus, laboratory test criteria and test criteria for on-site use were developed. Building on the knowledge gained with respect to the long-term stability of backfillings, the damage potential of already existing BHE can be also assessed.
In Germany, there is only little information available on hazards to groundwater. The impact of vertical GSHP systems on groundwater and the resulting impairments are difficult to estimate and damage most often cannot be quantified (AD-HOC-AG Geologie 2011). Contaminations often occur for a short period of time only or even remain undetected. Drilling companies and owners do not have any interest in and authorities often do not have enough resources for expensive monitoring measures or on-site inspections. Moreover, risks associated with groundwater usually become apparent only, if the water is used as drinking water (Butscher et al. 2010). Negative impacts of shallow geothermal energy on groundwater quality were the subject of many studies: Bonte et al. (2011) distinguished impacts of thermal, chemical, microbiological, and hydrological nature. According to Hähnlein et al. (2013), however, the existing knowledge is insufficient to assess the environmental impact on groundwater. Hence, there is a need for further environmental impact research and assessments through field and in situ experiments (Brielmann et al. 2011; Hähnlein et al. 2013).
In some cases, insufficient preliminary investigations, the use of improper materials, or poor decision making facilitated damage events in the past. Minimising risks includes not only the adoption of guidelines, but also the verification of compliance on construction sites. According to Sonnenfroh (personal communication 2017), about 10% of their drilling activities are inspected by the local water authorities, which appears to be appropriate. Hence, we strongly recommend countrywide, regular on-site quality controls (QC) of on-site operations of drilling companies and plumbers to verify compliance with existing guidelines.
Events with a damage amount of more than 500,000 Euros are rare in Germany. In most cases, these damages were caused by aquifers that were connected by incomplete and leaky backfilling. Damages running into the millions were almost entirely caused by swellable minerals at the Keuper-Muschelkalk boundary. Due to the difficult geological and hydrogeological conditions in Baden-Württemberg, the probability of a damage event here is increased. As a countermeasure, the state of Baden-Württemberg has introduced the guideline “Leitlinien Qualitätssicherung Erdwärmesonde” (LQS EWS 2011, Guidelines for quality assurance of downhole borehole heat exchangers). Since then, no further damage events have occurred in Baden-Württemberg. Additionally, Harter et al. (2017) published an information flyer, where they clear up with 21 misunderstandings regarding GSHP systems. In order to prevent damage even more effectively in the future, the following activities are proposed:
Systematic quantification of damage events in Germany
Drilling companies or owners should be obliged to report damages directly to the responsible authority. Systematic and central collection of those data would reveal important information on the efficiency of quality assurance (QA) and quality control (QC) measures. Additionally, the probability of occurrence could be calculated in relation to geological and hydrogeological conditions. The population’s confidence in vertical GSHP systems can only be restored by transparent damage reporting. Only exact and reliable statistics can prove the low hazard potential of this technology.
Ongoing development of GIS
In order to assess various risks, comprehensive information on potential geological and hydrogeological hazards is required. The development of countrywide hazard maps should be given a high priority. Using precise GIS, a local specific, risk-oriented approval procedure can be established.
Training of decision makers and staff
Foresighted planning under careful consideration of geological and hydrogeological conditions.
Quality-oriented and quality-controlled construction using site-specific materials and methods with a comprehensive documentation of all production steps and proper and continuous maintenance (Sass et al. 2014).
Drilling teams should be able to recognise potential hazards in order to immediately take appropriate countermeasures.
Regional and hazard-specific guidelines
Building on the success achieved, state guidelines have to be adapted to take latest knowledge and methods into consideration. Intensive information exchange between all parties on relevant experiences and best practices would be desirable. Instead of 16 different guidelines for each federal state, authorities should focus on adopting cross-border, risk-specific, national standardised guidelines. Preliminary investigations, approval procedures, and specific requirements could be adapted to local conditions.
In high-risk areas, vertical GSHP systems should be subject to strict quality measures or approval might be refused. Despite all potential risks, however, it would be not in the public interest to restrict the use of a technology that undoubtedly has economic and ecological benefits just because of previous (unnecessary) damage events. Thus, cross-border quality assurance has to be given highest priority. Negative impacts on groundwater and its quality should be investigated in detail in the laboratory and in the field. Especially the quality of backfilling materials and backfilling procedure, appropriate monitoring systems, and appropriate drilling techniques have to be improved.
PF and PB designed the study and developed the methodology. PF drafted the final manuscript. PB offered supervision for the research and guidance with the interpretation of results. All authors read and approved the final manuscript.
We would like to thank Manuel Grimm for his comments and suggestions supporting our efforts. The constructive comments of two anonymous reviewers are also gratefully acknowledged.
The authors declare that they have no competing interests.
Availability of data and materials
All relevant data and material are presented in the main paper.
Springer Nature remains neutral with regard to jurisdictional claims in published maps and institutional affiliations.
Open AccessThis article is distributed under the terms of the Creative Commons Attribution 4.0 International License (http://creativecommons.org/licenses/by/4.0/), which permits unrestricted use, distribution, and reproduction in any medium, provided you give appropriate credit to the original author(s) and the source, provide a link to the Creative Commons license, and indicate if changes were made.
- AD-HOC-AG Geologie. Fachbericht zu bisher bekannten Auswirkungen geothermischer Vorhaben in den Bundesländern. Staatliche geologische Dienste Deutschlands, Wiesbaden; 2011.Google Scholar
- AD-HOC-AG Hydrogeologie. Empfehlungen für die Anforderungen an die hydraulische Durchlässigkeit des Systems Erdwärmesonde. Staatliche geologische Dienste Deutschlands; 2015.Google Scholar
- Bassetti S, Rohner E, Signorelli S. Dokumentation von Schadensfällen bei Erdwärmesonden. EnergieSchweiz; 2006.Google Scholar
- Bayer P, Saner D, Bolay S, Rybach L, Blum P. Greenhouse gas emission savings of ground source heat pump systems in Europe: a review. Renew Sustain Energy Rev. 2012;16(2):1256–67. doi:10.1016/j.rser.2011.09.027.View ArticleGoogle Scholar
- Blum P, Campillo G, Kölbel T. Techno-economic and spatial analysis of vertical ground source heat pump systems in Germany. Energy. 2011;36(5):3002–11. doi:10.1016/j.energy.2011.02.044.View ArticleGoogle Scholar
- Blum P, Campillo G, Münch W, Kölbel T. CO2 savings of ground source heat pump systems—a regional analysis. Renew Energy. 2010;35(1):122–7. doi:10.1016/j.renene.2009.03.034.View ArticleGoogle Scholar
- Bonte M, Stuyfzand PJ, Hulsmann A, van Beelen P. Underground thermal energy storage: environmental risks and policy developments in the Netherlands and European Union. Ecol Soc. 2011;16:22.View ArticleGoogle Scholar
- Brielmann H, Lueders T, Schreglmann K, Ferraro F, Avramov M, Hammerl V, Blum P, Bayer P, Griebler C. Oberflächennahe Geothermie und ihre potenziellen Auswirkungen auf Grundwasserökosysteme. Grundwasser. 2011; (16): 77–91.Google Scholar
- Butscher C, Breuer S, Blum P. Swelling laws for clay-sulfate rocks revisited. Bull Eng Geol Environ. 2016a;63:707. doi:10.1007/s10064-016-0986-z.Google Scholar
- Butscher C, Huggenberger P, Auckenthaler A, Bänninger D. Risikoorientierte Bewilligung von Erdwärmesonden. Grundwasser. 2010; 16(1): 13–24. doi: 10.1007/s00767-010-0154-5.Google Scholar
- Butscher C, Mutschler T, Blum P. Swelling of clay-sulfate rocks: a review of processes and controls. Rock Mech Rock Eng. 2016b;49(4):1533–49. doi:10.1007/s00603-015-0827-6.View ArticleGoogle Scholar
- BVG. Richtlinien und Leitfäden zur Oberflächennahen Geothermie. 2014. http://www.geothermie.de/service/publikationen/leitfaeden-und-richtlinien-der-bundeslaender.html. Accessed 9 Apr 2016.
- BWP. Trotz Ölpreisverfall: Wärmepumpenabsatz 2015 stabil; 2016.Google Scholar
- FAZ. Erdwärme-Bohrpanne kostet halbe Million Euro. Frankfurter Allgemeine Zeitung 2010; 2010.Google Scholar
- Goldscheider N, Bechtel TD. Editors’ message: the housing crisis from underground—damage to a historic town by geothermal drillings through anhydrite, Staufen, Germany. Hydrogeol J. 2009;17(3):491–3. doi:10.1007/s10040-009-0458-7.View ArticleGoogle Scholar
- Grimm M, Stober I, Kohl T, Blum P. Schadensfallanalyse von Erdwärmesondenbohrungen in Baden-Württemberg. Grundwasser. 2014; 19(4): 275–286. doi: 10.1007/s00767-014-0269-1.Google Scholar
- Hähnlein S, Bayer P, Ferguson G, Blum P. Sustainability and policy for the thermal use of shallow geothermal energy. Energy Policy. 2013;59:914–25. doi:10.1016/j.enpol.2013.04.040.View ArticleGoogle Scholar
- Hähnlein S, Blum P, Bayer P. Oberflächennahe Geothermie—aktuelle rechtliche Situation in Deutschland. Grundwasser. 2011;16(2):69–75. doi:10.1007/s00767-011-0162-0.View ArticleGoogle Scholar
- Harter K, Lorinser B, Sawillion M, Stober I. Erdwärmesonden: Erdwärme erfolgreich nutzen! 21 Missverständnisse. Ministerium für Umwelt, Klima und Energiewirtschaft Baden-Württemberg; 2017.Google Scholar
- Klotzbücher T, Kappler A, Straub KL, Haderlein SB. Biodegradability and groundwater pollutant potential of organic anti-freeze liquids used in borehole heat exchangers. Geothermics. 2007;36(4):348–61. doi:10.1016/j.geothermics.2007.03.005.View ArticleGoogle Scholar
- Kübert M, Walker-Hertkorn S, Blum P, Bayer P, Hähnlein S. Praktische Hinweise zur Genehmigungspraxis der thermischen Nutzung des Untergrundes. bbr Sonderheft Geothermie: 8–13; 2009.Google Scholar
- LGRB. Geologische Untersuchungen von Baugrundhebungen im Bereich des Erdwärmesondenfeldes beim Rathaus in der historischen Altstadt von Staufen i. Br; 2010.Google Scholar
- LGRB. Zweiter Sachstandsbericht zu den seit dem 01.03.2010 erfolgten Untersuchungen im Bereich des Erdwärmesondenfeldes beim Rathaus in der historischen Altstadt von Staufen i. Br. Landesamt für Geologie, Rohstoffe und Bergbau Baden-Württemberg; 2012.Google Scholar
- LGRB. Geologische Untersuchungen von Baugrundhebungen im nordöstlichen Stadtgebiet von Böblingen (Hebungsgebiet “Nord”): Sachstandsbericht. Landesamt für Geologie, Rohstoffe und Bergbau Baden-Württemberg; 2016.Google Scholar
- Lowe M. Subsidence in sedimentary basins due to groundwater withdrawal for geothermal energy development. Utah Geol Survey. 2012.Google Scholar
- LQS EWS. Leitlinien Qualitätssicherung Erdwärmesonden (LQS EWS). Ministerium für Umwelt, Klima und Energiewirtschaft Baden-Württemberg, Stuttgart; 2011.Google Scholar
- Ondreka J, Rüsgen MI, Stober I, Czurda K. GIS-supported mapping of shallow geothermal potential of representative areas in south-western Germany—possibilities and limitations. Renew Energy. 2007;32(13):2186–200. doi:10.1016/j.renene.2006.11.009.View ArticleGoogle Scholar
- RAG. Glück auf. Zukunft: Nachhaltig handeln—Die RAG stellt Umwelt, Wirtschaft und Soziales in den Fokus. 2014. https://www.rag.de/fileadmin/rag_de/user_upload/DOKUMENTE-DWNLD/Downloads_Publikationen/2014_10_06_Glueck_auf_Zukunft.pdf. Accessed 24 Jan 2017.
- RAG-Stiftung. Ewigkeitsaufgaben. 2015. http://www.rag-stiftung.de/ewigkeitsaufgaben/. Accessed 8 Mar 2016.
- Riegger M, Rolker J, Stober I, Haist M, Schlager P, Zorn R, Huttenloch P, Steger H, Eckhardt J-D, Zemann M. EWS-tech: Weiterentwicklung der Erdwärmesonden-Technologie; 2016.Google Scholar
- Ruch C, Wirsing G. Erkundung und Sanierungsstrategien im Erdwärmesonden-Schadensfall Staufen i. Br. geotechnik. 2013; 36(3):147–159. doi: 10.1002/gete.201300005.Google Scholar
- Rumohr S. Nutzung der Oberflächennahen Geothermie in Hessen - Ist das Ende des Booms erreicht? Hessisches Landesamt für Umwelt und Geologie, Wiesbaden; 2008.Google Scholar
- Sachs O, Eberhard M. Erdgasausbruch bei einer Erdwärmesondenbohrung in Rothrist-Buchrain—ein Erfahrungsbericht. Swiss Bull. angewandte Geowissenschaften. 2010; 15(1): 43–51.Google Scholar
- Santi PM, McCray JE, Martens JL. Investigating cross-contamination of aquifers. Hydrogeol J. 2005;14(1):51–68. doi:10.1007/s10040-004-0403-8.Google Scholar
- Sass I, Brehm D, Coldewey WG, Dietrich J, Klein R, Kellner T, Kirschbaum B, Lehr C, Marek A, Mielke P. Empfehlung Oberflächennahe Geothermie—Planung, Bau, Betrieb und Überwachung-EA Geothermie. Berlin: Ernst & Sohn; 2014.Google Scholar
- Sass I, Burbaum U. Damage to the historic town of Staufen (Germany) caused by geothermal drillings through anhydrite-bearing formations. AC. 2012. doi:10.3986/ac.v39i2.96.Google Scholar
- Sass I, Burbaum U. Geothermische Bohrungen in Staufen im Breisgau: Schadensursachen und Perspektiven. geotechnik. 2010; 35(3): 198–205. doi: 10.1002/gete.201100018
- Schäfer I, Rumohr S. Sichere Erdwärmeprojekte durch Geofachdaten. bbr Fachmagazin für Brunnen- und Leitungsbau, Sonderheft Oberflächennahe Geothermie:6–12; 2011.Google Scholar
- Schulz R, Agemar T, Alten J-A, Wirth LW. Development of an Internet based geothermal information system for Germany. Erdöl Erdgas Kohle; 2007.Google Scholar
- Sivasakthivel T, Murugesan K, Sahoo PK. Potential reduction in CO2 emission and saving in electricity by ground source heat pump system for space heating applications—a study on Northern Part of India. Procedia Eng. 2012;38:970–9. doi:10.1016/j.proeng.2012.06.123.View ArticleGoogle Scholar
- Stadt Staufen. Presseerklärung vom 17. September 2012 der Stadt Staufen und der Interessengemeinschaft der Riss-Geschädigten GbR (IGR); 2012.Google Scholar
- Stadt Staufen. Presseerklärung zu den Hebungsrissen; 2016.Google Scholar
- StZ. Erdhebungen: Wasserrohre gehen zu Bruch: Böblingen: Stadt und Stadtwerke melden Schäden. Stuttgarter Zeitung; 2015.Google Scholar
- TS. Toteis-Theorie in der Lindenstraße. 2016. http://tegernseerstimme.de/toteis-theorie-in-der-lindenstrasse/225969.html. Accessed 31 Mar 2017.
- Wrede V. Die Bohrungshavarie Kamen-Wasserkurl aus geowissenschaftlicher Sicht. In: Frenz W, Preuße A (eds) Geothermie—Risikobeherrschung und Stand der Technik, Perspektiven und Fördermöglichkeiten: 12. Aachener Altlasten- und Bergschadenkundliches Kolloquium; GDMB, Clausthal-Zellerfeld 123; 2010.Google Scholar
- WN. Boden tat sich auf: Millionenschaden nach Erdwärme-Bohrung. Westfälische Nachrichten; 2009.Google Scholar