From: Making use of geothermal brine in Indonesia: binary demonstration power plant Lahendong/Pangolombian

Temperatures | Mass flow rates | Electrical power | ||||
---|---|---|---|---|---|---|

Brine supply |
T_{geo,i} °C
| 172.5 |
ṁ_{geo} in kg/s
| 32.0 | ||

T_{geo,o} °C
| 142.5 | |||||

Hot water cycle |
T_{HW,i} in °C
| 165.0 |
ṁ̇_{HW} in kg/s
| 32.0 |
P_{el,HP} in kW
| 8.9 |

T_{HW,o} in °C
| 135.0 | |||||

Cooling water cycle |
T_{a,i} in °C
| 25.0 |
ṁ_{a} in kg/s
| 221.4 |
P_{el,F} in kW
| 25.4 |

T_{a,o} in °C
| 40.7 | |||||

T_{CW,i} in °C
| 34.0 |
ṁ_{CW} in kg/s
| 86.1 |
P_{el,CP} in kW
| 16.2 | |

T_{CW,o} in °C
| 44.0 | |||||

ORC-unit |
T_{ev} in °C
| 142.6 |
ṁ̇_{WF} in kg/s
| 9.5 |
P_{el,G} in kW
| 499.4 |

T_{cd} in °C
| 49.4 |
P_{el,P} in kW
| 23.4 | |||

Net power |
P_{el,Net} in kW
| 425.5 |